I am having a question regarding Pop Up Alarm messages for Hotel rooms. We have a KNX project for a hotel and we have install a Sledgehammer Server. We have create the Users such as Reception and Room's Users . Inside each Room we have 3 different push buttons for 3 different alarm functions which are: Do not Disturb , Make Up My Room and Room Service. What we need to do is anytime the customer of each room when pressing one of these buttons the Reception will receive a pop Up Alarm message on the screen . I have tried to make this configuration but I didn't get any pop-up messages when pressing on of these three buttons. Any ideas how we can make this work?
Hello. In last 4.5.8 version of bOS I noticed "bad UTF encoding" in KNX import section. In our language we use lots of accent word and in past version it was fine but in last it is doing this:
Maybe I am missing some settings but I have country set to SK and also user language to Slovakian.
is it possible to save users' activity in a log file?
In a form like Date-Time-Action?
I'm using sledgehammer server and i want to do it in a Hotel KNX installation.
I am a beginner with the Comfortclick and I have a simple question about the status of the devices. Where can I configure the status? I just found the parameter value.
The same thing happened to me with other kind of devices like temperature setpoints, shades, and more things...
Thanks a lot!
I looking for a way to activate a scene from Comfortclick with a KNX-pushbutton in a project that i'm working on.
Any ideas how i can use the button as a trigger for a scene?
I've configured the physical address in knx for a Jigsaw to be 1.1.63, as the last device before a line repeater.
The issue is that when I open the bus monitor in ETS, I see a lot of traffic coming from 1.1.64, which is the line repeater, but corresponds to the Jigsaw.
Why isn't it using the address I configured?
Thanks in advance
Our client wanted to change ventilation speeds from the thermostat. Ventilation runs on Modbus everything else is on KNX bus.
This may be a really stupid question but... i found that when i put a value for 1byte in bOS 1 then KNX sees it as 3 and value 2 as 5. But in bOS it shows the correct values. Ventilation has 3 speeds that we control (0 is for away, 1 is home, 2 is guests) I made some screenshots.
Shows as correct value in bOS
But in KNX sees it as 3 and value 2 as 5 in knx
Is this normal or am i missing something?
I got it working though by changing the values in the Thermostat to 3 and 5, there is no problem with value 0 :) . So now every thermostat shows the correct status and from every thermostat they can change the ventilation speeds. But I find it weird that it changes the values like that.
Customer support service by UserEcho