I try many times but the 1 byte DPT 20.102 HVAC mode is not imported.
The datapoint is visible and correctely identified in the first step, but in the final step the DPT not present
In finaly the value is not imported to the bOS.
Hello, I have all my KNX devices at home connected via BOS to Alexa - about 70 devices. All worked well, until suddenly Alexa stopped responding to all devices. i.e. - When I ask Alexa to 'turn on' a device, it says that the device is not responding - this is the same situation with all my KNX devices. To clarify, BOS works well from the app and also Alexa works well with other devices not connected via BOS. Any idea?
I am trying to solve issue where I have KNX bus behind NAT with static public IP and forwarding is working, but UDP protocol is blocked by provider. (I called the provider, they told me there is nothing they can do, I know is stupid, so here we go) So I standing in front of issue that I cannot connect to KNX bus because is only over UDP port. Is here anybody who already solve this issue and is willing share the solution?
PS.: On site Jigsaw is not an option because is only two thermostat that controll two rooms. Time to time disconnection is acceptable because of NAT connection.
Hi To Alll
im trying to create a simple knx thermostat with the setpoint up and down, and i unable to find the optimal solution, also im trying to display the room temperature and when you press the up or down button to display the setpoint.
im using bosconfig 4.8.5.
Thanks in advance
Hello, does anyone know why the 3671 port doesn't work anymore on Bos controller even if there is a port forwarding? I need this for remote programming my KNX installation. It was working good so far since know. Also when the Bos configurator inform me that i need to update my controller when the window prompt me to, there is no update available.
Thanks in advance.
We've just receive the comfort click server yesterday and we've made our test , kindly be informed that we've found a problem such as the following points :-
1- We've create an account on comfort click .
2- We download B0S configuration and B0S server and B0S client.
3- Make configuration and link group address with buttons according to ETS project.
4- When we make check from mobile application or laptop not give any output to the relay.
5- Make full download to relay by using comfort click server.
I'll be waiting for your urgent reply as this project top top urgent.
I'm facing some issues with downloading my components with ETS5 and generate the ETS export file to import afterwards in bOS.
In bOS the Jigsaw KNX is std. CCJigsaw 0.0.1.
When I try to connect in ETS5 with CCJigsaw 192.168.1.16:3671 to Individual Address 0.0.1 for downloading my components I get the error: "The individual address is already in use by another device."
I was not able to add the Comfortclick in my topology.
Someone who can assist my with this?
Should I connect with USB directly to the module instead of connecting over wifi?
I'm trying something simple but seem to miss something.
I wan't to read the operating time from the ECG's in the dali gateway.
I gave the operating time there own knx adres but I can't read the values in bos ??
Customer support service by UserEcho