I try many times but the 1 byte DPT 20.102 HVAC mode is not imported.
The datapoint is visible and correctely identified in the first step, but in the final step the DPT not present
In finaly the value is not imported to the bOS.
Hello, I have all my KNX devices at home connected via BOS to Alexa - about 70 devices. All worked well, until suddenly Alexa stopped responding to all devices. i.e. - When I ask Alexa to 'turn on' a device, it says that the device is not responding - this is the same situation with all my KNX devices. To clarify, BOS works well from the app and also Alexa works well with other devices not connected via BOS. Any idea?
After upgrading bOS to the latest version (4.8.20), when I reboot the server (a clean reboot: Building/Reboot), the KNX conecction type sets itself automatically to KNX IP. I change it to KNXnet IP (Falcon), but with a new reboot, it changes back to KNX IP.
Is anyone experiencing this?
Hello. Is there any way to access the ETS project through comfortclick? On some occasion I have been told that it is possible but I cannot find a way to connect to the bus through ETS. Greetings
Hi to all,
i have a problem read max temperature from a thermostat.
Every time i add it to a frame, i get this error. It work's very well with min temperature and
Have anyone an idea how i can fix this?
Thermostat is an MDT Controller.
I'm learning the connection between a bOS and a device with KNX protocol.
How many devices can the bOS be connected to via KNX?
If you have a sample configuration of bOS and KNX device, please share it with me.
Thanks & Best Regards.
There are a couple of similar posts, but none really hits the nail on the head as maybe I have a different problem. BOS server version latest 4.8.14
The situation is very simple, I want to create three variables (date, time, timestamp) in BOS, which are then mapped or given the same addresses as KNX so BOS effectively populates the KNX addresses and issues the date and time to the KNX BUS. However, there are continues issues, despite several and lengthy testing performed
Current BOS variables created
Current KNX variables created in ETS5
Time, seems to be working fine
- First problem, the value type, KNX 11.001, allows for the time, but the time value is actually not populated by BOS
- Second problem, if status address is populated in the BOS variable it creates problems for BOS and the date is no longer transmitted/populated
- Third problem, the associated KNX variable, spits errors, despite being the same value type
Errors spit in transforming
- First problem, the time is not populated, only the hour of the time is, minutes and seconds are not populated
- Second problem, the KNX variable is not populated, not a single field
Customer support service by UserEcho