I am a beginner with the Comfortclick and I have a simple question about the status of the devices. Where can I configure the status? I just found the parameter value.
The same thing happened to me with other kind of devices like temperature setpoints, shades, and more things...
Thanks a lot!
I looking for a way to activate a scene from Comfortclick with a KNX-pushbutton in a project that i'm working on.
Any ideas how i can use the button as a trigger for a scene?
I've configured the physical address in knx for a Jigsaw to be 1.1.63, as the last device before a line repeater.
The issue is that when I open the bus monitor in ETS, I see a lot of traffic coming from 1.1.64, which is the line repeater, but corresponds to the Jigsaw.
Why isn't it using the address I configured?
Thanks in advance
Our client wanted to change ventilation speeds from the thermostat. Ventilation runs on Modbus everything else is on KNX bus.
This may be a really stupid question but... i found that when i put a value for 1byte in bOS 1 then KNX sees it as 3 and value 2 as 5. But in bOS it shows the correct values. Ventilation has 3 speeds that we control (0 is for away, 1 is home, 2 is guests) I made some screenshots.
Shows as correct value in bOS
But in KNX sees it as 3 and value 2 as 5 in knx
Is this normal or am i missing something?
I got it working though by changing the values in the Thermostat to 3 and 5, there is no problem with value 0 :) . So now every thermostat shows the correct status and from every thermostat they can change the ventilation speeds. But I find it weird that it changes the values like that.
I'd like to use the night mode in the buttons (light up and night).
and at the same time i wan't to have the lighting in the bedroom area (toilet, bedrooms, halway,..) to work at ca. 40%.
All lights are DALI dimmable.
I made a group 3/3/4 night buttons where i put the 4(general) LED - brightness mode in.
What do i have to do in bosconfig for the nightmode buttons and what for the lights to go max. 40%?
I have an important question,, so plz help to answer it,,
I have hotel project,, the owner needs to know if the rooms are (occupied / empty) as a simple solution, using a KNX 4 binary input modules,,
so my question is can i integrate these knx modules with jigsaw, to read/know each room status as (occupied /empty)??
Note: in this KNX system, I will use KNX Power Supply and KNX 4 binary input modules..
I have some some dimming lights (controlled buy dali gateway), they are programmed in ETS and working fine.
Now i'm trying to control theme with comfort click without succes.
I have the following adresses:
3/4/0 switch (switch)
3/4/1 dimming (dimming control)
3/4/2 value (percentage 0-100%)
3/4/3 status (switch)
I used in comfort click the following adress:
Address: 3/4/0 switch
status address: 3/4/2
the slide goes directly back to 0
the light does nothing
Customer support service by UserEcho