I'm using a electrical energy counter, the values recived are in W, mA, mV, and I want to convert to KW, A, and V.
How I can convert these values?
You can either go through a task calculation or a log scalling...
Here, one of my exemple for the power value
where to make some calculation through a task
I receive these values (4bytes) from KNX device, and I show as labels in a panel, there is no "Scalling" option as yu showed me.
How can I change scalling value when I receive values from a KNX Device.
Thank you very much.
The scalling is only available if you go through a "log", as shown in the top picture above.
If you don't want/need to go through a log, you will need to use a task calculation to convert from A to mA, and link the label to the calculation output, not to the knx device output value
here, as an example, how to multiply x1000 a current input value:
Hope this helps
Customer support service by UserEcho